RQCEQ280PY13 | RQCEQ360PY13 | RQCEQ460PY13 | RQCEQ500PY13 | RQCEQ540PY13 | RQCEQ636PY13 | RQCEQ712PY13 | RQCEQ744PY13 | RQCEQ816PY13 | RQCEQ848PY13 | |||||
---|---|---|---|---|---|---|---|---|---|---|---|---|---|---|

System | Outdoor unit module 1 | RQEQ140P3 | RQEQ180P3 | RQEQ140P3 | RQEQ140P3 | RQEQ180P3 | RQEQ212P3 | RQEQ140P3 | RQEQ140P3 | RQEQ180P3 | RQEQ212P3 | |||

Outdoor unit module 2 | RQEQ140P3 | RQEQ180P3 | RQEQ140P3 | RQEQ180P3 | RQEQ180P3 | RQEQ212P3 | RQEQ180P3 | RQEQ180P3 | RQEQ212P3 | RQEQ212P3 | ||||

Outdoor unit module 3 | RQEQ180P3 | RQEQ180P3 | RQEQ180P3 | RQEQ212P3 | RQEQ180P3 | RQEQ212P3 | RQEQ212P3 | RQEQ212P3 | ||||||

Outdoor unit module 4 | RQEQ212P3 | RQEQ212P3 | RQEQ212P3 | RQEQ212P3 | ||||||||||

Capacity range | HP | 10 | 13 | 16 | 18 | 20 | 22 | 24 | 26 | 28 | 30 | |||

Maximum number of connectable indoor units | 21 | 28 | 34 | 39 | 43 | 47 | 52 | 56 | 60 | 64 | ||||

Indoor index connection | Min. | 140 | 180 | 230 | 250 | 270 | 318 | 356 | 372 | 408 | 424 | |||

Nom. | 280 | 360 | 500 | 500 | 540 | 636 | 712 | 744 | 816 | 848 | ||||

Max. | 364 | 468 | 598 | 650 | 702 | 827 | 926 | 967.0 | 1,061 | 1,102 | ||||

Sound power level | Cooling | Nom. | dBA | 82 | 87 | 87 | 88 | 89 | 93 | 92 | 93 | 95 | 95 | |

Refrigerant | Type | R-410A | R-410A | R-410A | R-410A | R-410A | R-410A | R-410A | R-410A | R-410A | R-410A | |||

GWP | 2,087.5 | 2,087.5 | 2,087.5 | 2,087.5 | 2,087.5 | 2,087.5 | 2,087.5 | 2,087.5 | 2,087.5 | 2,087.5 | ||||

Piping connections | Liquid | Type | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | ||

OD | mm | 9.52 | 12.7 | 12.7 | 15.9 | 15.9 | 15.9 | 15.9 | 19.1 | 19.1 | 19.1 | |||

Gas | Type | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | |||

OD | mm | 22.2 | 25.4 | 28.6 | 28.6 | 28.6 | 28.6 | 28.6 | 34.9 | 34.9 | 34.9 | |||

Total piping length | System | Actual | m | 300 | 300 | 300 | 300 | 300 | 300 | 300 | 300 | 300 | 300 | |

Level difference | OU - IU | Outdoor unit in highest position | m | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | |

Discharge gas | OD | mm | 19.1 | 19.1 | 22.2 | 22.2 | 22.2 | 25.4 | 25.4 | 25.4 | 28.6 | 28.6 | ||

Type | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | Braze connection | ||||

Power supply | Name | Y1 | Y1 | Y1 | Y1 | Y1 | Y1 | Y1 | Y1 | Y1 | Y1 | |||

Phase | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | 3~ | ||||

Frequency | Hz | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | 50 | |||

Voltage | V | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | 400 | |||

Notes | (1) - Cooling: indoor temp. 27°CDB, 19°CWB; outdoor temp. 35°CDB; equivalent piping length: 7.5m; level difference: 0m | (1) - Cooling: indoor temp. 27°CDB, 19°CWB; outdoor temp. 35°CDB; equivalent piping length: 7.5m; level difference: 0m | (1) - Cooling: indoor temp. 27°CDB, 19°CWB; outdoor temp. 35°CDB; equivalent piping length: 7.5m; level difference: 0m | |||||||||||

(2) - Heating: indoor temp. 20°CDB; outdoor temp. 7°CDB, 6°CWB; equivalent refrigerant piping: 7.5m; level difference: 0m | (2) - Heating: indoor temp. 20°CDB; outdoor temp. 7°CDB, 6°CWB; equivalent refrigerant piping: 7.5m; level difference: 0m | (2) - Heating: indoor temp. 20°CDB; outdoor temp. 7°CDB, 6°CWB; equivalent refrigerant piping: 7.5m; level difference: 0m | ||||||||||||

(3) - TOCA means the total value of each OC set. | (3) - TOCA means the total value of each OC set. | (3) - TOCA means the total value of each OC set. | (3) - TOCA means the total value of each OC set. | (3) - TOCA means the total value of each OC set. | (3) - TOCA means the total value of each OC set. | (3) - TOCA means the total value of each OC set. | (3) - TOCA means the total value of each OC set. | (3) - TOCA means the total value of each OC set. | (3) - TOCA means the total value of each OC set. | |||||

(4) - MSC means the maximum current during start up of the compressor | (4) - MSC means the maximum current during start up of the compressor | (4) - MSC means the maximum current during start up of the compressor | (4) - MSC means the maximum current during start up of the compressor | (4) - MSC means the maximum current during start up of the compressor | (4) - MSC means the maximum current during start up of the compressor | (4) - MSC means the maximum current during start up of the compressor | (4) - MSC means the maximum current during start up of the compressor | (4) - MSC means the maximum current during start up of the compressor | (4) - MSC means the maximum current during start up of the compressor | |||||

(5) - Voltage range: units are suitable for use on electrical systems where voltage supplied to unit terminal is not below or above listed range limits. | (5) - Voltage range: units are suitable for use on electrical systems where voltage supplied to unit terminal is not below or above listed range limits. | (5) - Voltage range: units are suitable for use on electrical systems where voltage supplied to unit terminal is not below or above listed range limits. | ||||||||||||

(6) - Maximum allowable voltage range variation between phases is 2%. | (6) - Maximum allowable voltage range variation between phases is 2%. | (6) - Maximum allowable voltage range variation between phases is 2%. | (6) - Maximum allowable voltage range variation between phases is 2%. | (6) - Maximum allowable voltage range variation between phases is 2%. | (6) - Maximum allowable voltage range variation between phases is 2%. | (6) - Maximum allowable voltage range variation between phases is 2%. | (6) - Maximum allowable voltage range variation between phases is 2%. | (6) - Maximum allowable voltage range variation between phases is 2%. | (6) - Maximum allowable voltage range variation between phases is 2%. | |||||

(7) - Select wire size based on the larger value of MCA or TOCA | (7) - Select wire size based on the larger value of MCA or TOCA | (7) - Select wire size based on the larger value of MCA or TOCA | (7) - Select wire size based on the larger value of MCA or TOCA | (7) - Select wire size based on the larger value of MCA or TOCA | (7) - Select wire size based on the larger value of MCA or TOCA | (7) - Select wire size based on the larger value of MCA or TOCA | (7) - Select wire size based on the larger value of MCA or TOCA | (7) - Select wire size based on the larger value of MCA or TOCA | (7) - Select wire size based on the larger value of MCA or TOCA | |||||

(8) - MFA is used to select the circuit breaker and the ground fault circuit interrupter (earth leakage circuit breaker). | (8) - MFA is used to select the circuit breaker and the ground fault circuit interrupter (earth leakage circuit breaker). | (8) - MFA is used to select the circuit breaker and the ground fault circuit interrupter (earth leakage circuit breaker). | ||||||||||||

(9) - Contains fluorinated greenhouse gases | (9) - Contains fluorinated greenhouse gases | (9) - Contains fluorinated greenhouse gases | (9) - Contains fluorinated greenhouse gases | (9) - Contains fluorinated greenhouse gases | (9) - Contains fluorinated greenhouse gases | (9) - Contains fluorinated greenhouse gases | (9) - Contains fluorinated greenhouse gases | (9) - Contains fluorinated greenhouse gases | (9) - Contains fluorinated greenhouse gases |