FTX20GV1B / RX20GV1B | FTX25GV1B / RX25GV1B | FTX35GV1B / RX35GV1B | FTX50GV1B / RX50G2V1B | FTX50GV1B / RX50G3V1B | FTX60GV1B / RX60G2V1B | FTX60GV1B / RX60G3V1B | FTX71GV1B / RX71GV1B | FTX71GV1B / RX71GV1B9 | ||||
---|---|---|---|---|---|---|---|---|---|---|---|---|

Cooling capacity | Min. | kW | 1.3 | 1.3 | 1.3 | 1.7 | 1.7 | 1.7 | 1.7 | 2.3 | 2.3 | |

Nom. | kW | 2.0 (3) | 2.5 (3) | 3.2 (3) | 5.0 (3) | 5.0 (2) | 6.0 (3) | 6.0 (2) | 7.1 (3) | 7.1 (2) | ||

Max. | kW | 2.6 | 3.0 | 3.8 | 6.0 | 6.0 | 6.7 | 6.7 | 8.5 | 8.5 | ||

Heating capacity | Min. | kW | 1.3 | 1.3 | 1.3 | 1.7 | 1.7 | 1.7 | 1.7 | 2.3 | 2.3 | |

Nom. | kW | 2.5 (4) | 2.8 (4) | 3.4 (4) | 5.8 (4) | 5.8 (3) | 7.0 (4) | 7.0 (3) | 8.2 (4) | 8.2 (3) | ||

Max. | kW | 3.5 | 4.0 | 4.8 | 7.7 | 7.7 | 8.0 | 8.0 | 10.2 | 10.2 | ||

Nominal efficiency | EER | 3.62 | 3.38 | 3.37 | 3.23 | 3.23 | 3.02 | 3.02 | 3.02 | 3.02 | ||

COP | 3.90 | 3.68 | 3.74 | 3.63 | 3.63 | 3.43 | 3.43 | 3.22 | 3.22 | |||

Annual energy consumption | kWh | 275 | 370 | 470 | 775 | 775 | 995 | 995 | 1,175 | 1,175 | ||

Energy labeling Directive | Cooling | A | A | A | A | A | B | B | B | B | ||

Heating | A | A | A | A | A | B | B | C | C | |||

Space cooling | Capacity | Pdesign | kW | 5.00 | 6.00 | 7.10 | ||||||

Energy efficiency class | A+ | A | B | |||||||||

SEER | 5.63 | 5.10 | 4.93 | |||||||||

Annual energy consumption | kWh/a | 311 | 412 | 504 | ||||||||

Space heating (Average climate) | Capacity | Pdesign | kW | 4.60 | 4.80 | 6.50 | ||||||

Energy efficiency class | A+ | A | A | |||||||||

SCOP/A | 4.08 | 3.74 | 3.50 | |||||||||

Annual energy consumption | kWh/a | 1,578 | 1,795 | 2,593 | ||||||||

Piping connections | Drain | OD | mm | 18.0 | 18.0 | 18.0 | 18.0 | 18.0 | 18.0 | |||

Gas | OD | mm | 12.7 | 12.7 | 12.70 | 12.70 | 15.9 | 15.9 | ||||

Liquid | OD | mm | 6.35 | 6.35 | 6.35 | 6.35 | 6.35 | 6.35 | ||||

Notes | (1) - Energy label: scale from A (most efficient) to G (less efficient) | (1) - Energy label: scale from A (most efficient) to G (less efficient) | (1) - Energy label: scale from A (most efficient) to G (less efficient) | (1) - Energy label: scale from A (most efficient) to G (less efficient) | (1) - EER/COP according to Eurovent 2012, for use outside EU only | (1) - Energy label: scale from A (most efficient) to G (less efficient) | (1) - EER/COP according to Eurovent 2012, for use outside EU only | (1) - Energy label: scale from A (most efficient) to G (less efficient) | (1) - EER/COP according to Eurovent 2012, for use outside EU only | |||

(2) - Annual energy consumption: based on average use of 500 running hours per year at full load (nominal conditions) | (2) - Annual energy consumption: based on average use of 500 running hours per year at full load (nominal conditions) | (2) - Annual energy consumption: based on average use of 500 running hours per year at full load (nominal conditions) | (2) - Cooling: indoor temp. 27°CDB, 19.0°CWB; outdoor temp. 35°CDB, 24°CWB; equivalent piping length: 5m (horizontal) | (2) - Cooling: indoor temp. 27°CDB, 19.0°CWB; outdoor temp. 35°CDB, 24°CWB; equivalent piping length: 5m (horizontal) | (2) - Cooling: indoor temp. 27°CDB, 19.0°CWB; outdoor temp. 35°CDB, 24°CWB; equivalent piping length: 5m (horizontal) | |||||||

(3) - Cooling: indoor temp. 27°CDB, 19°CWB; outdoor temp. 35°CDB, 24°CWB; equivalent piping length: 5m (horizontal) | (3) - Cooling: indoor temp. 27°CDB, 19°CWB; outdoor temp. 35°CDB, 24°CWB; equivalent piping length: 5m (horizontal) | (3) - Cooling: indoor temp. 27°CDB, 19°CWB; outdoor temp. 35°CDB, 24°CWB; equivalent piping length: 5m (horizontal) | (3) - Cooling: indoor temp. 27°CDB, 19.0°CWB; outdoor temp. 35°CDB, 24°CWB; equivalent piping length: 5m (horizontal) | (3) - Heating: indoor temp. 20°CDB, outdoor temp. 7°CDB, 6°CWB; equivalent refrigerant piping: 5m; level difference: 0m. High fan speed indoor unit | (3) - Cooling: indoor temp. 27°CDB, 19.0°CWB; outdoor temp. 35°CDB, 24°CWB; equivalent piping length: 5m (horizontal) | (3) - Heating: indoor temp. 20°CDB; outdoor temp. 7°CDB, 6°CWB; equivalent refrigerant piping: 5m | (3) - Cooling: indoor temp. 27°CDB, 19.0°CWB; outdoor temp. 35°CDB, 24°CWB; equivalent piping length: 5m (horizontal) | (3) - Heating: indoor temp. 20°CDB; outdoor temp. 7°CDB, 6°CWB; equivalent refrigerant piping: 5m | ||||

(4) - Heating: indoor temp. 20°CDB; outdoor temp. 7°CDB, 6°CWB; equivalent refrigerant piping: 5m | (4) - Heating: indoor temp. 20°CDB; outdoor temp. 7°CDB, 6°CWB; equivalent refrigerant piping: 5m | (4) - Heating: indoor temp. 20°CDB; outdoor temp. 7°CDB, 6°CWB; equivalent refrigerant piping: 5m | (4) - Heating: indoor temp. 20°CDB, outdoor temp. 7°CDB, 6°CWB; equivalent refrigerant piping: 5m; level difference: 0m. High fan speed indoor unit | (4) - Nominal efficiency: cooling at 35°/27° nominal load, heating at 7°/20° nominal load | (4) - Heating: indoor temp. 20°CDB, outdoor temp. 7°CDB, 6°CWB; equivalent refrigerant piping: 5m; level difference: 0m. High fan speed indoor unit | (4) - Nominal efficiency: cooling at 35°/27° nominal load, heating at 7°/20° nominal load | (4) - Heating: indoor temp. 20°CDB, outdoor temp. 7°CDB, 6°CWB; equivalent refrigerant piping: 5m; level difference: 0m. High fan speed indoor unit | (4) - Nominal efficiency: cooling at 35°/27° nominal load, heating at 7°/20° nominal load | ||||

(5) - Nominal efficiency: cooling at 35°/27° nominal load, heating at 7°/20° nominal load | (5) - Nominal efficiency: cooling at 35°/27° nominal load, heating at 7°/20° nominal load | (5) - Nominal efficiency: cooling at 35°/27° nominal load, heating at 7°/20° nominal load | (5) - Nominal efficiency: cooling at 35°/27° nominal load, heating at 7°/20° nominal load | (5) - Nominal efficiency: cooling at 35°/27° nominal load, heating at 7°/20° nominal load | (5) - Nominal efficiency: cooling at 35°/27° nominal load, heating at 7°/20° nominal load |